的保养注意点 Analysis of maintenance points of FRP purification tower
1. The circulating water pump should be turned on for 2 to 3 minutes before use, and then the fan should be turned off; when stopping, the circulating water pump should be stopped for 1 to 2 minutes before stopping the circulating water pump. When starting the pump, please note that the pump must not be reversed and must not run dry.
2. Regularly inspect and maintain water pumps, valves, pipelines, nozzles, filters, etc. to ensure the normal operation of the equipment.
3. In order to ensure the normal operation of the tower equipment, there must be a special person responsible for management. The fans and pumps should be checked regularly for normal operation, the spray pipes and air pipes are unblocked, the liquid level of the reservoir is normal, and the water supply float switch is normal. Whether the gas-liquid concentration is within the specified range, etc. If problems are found, they should be resolved in time.
4. Regularly inspect the FRP exhaust gas treatment equipment regularly every year to prevent problems before they occur.
5.The user performs concrete foundation construction according to the basic data provided by the glass fiber reinforced plastic purification tower manufacturer; this equipment should be installed on the concrete foundation that is more than 100㎜ above the ground;
6, supporting pipelines, valves, etc. must have a separate support, can not be fixed on the tower equipment;
7. Pay attention to protect the equipment during installation so as not to damage the body and exposed parts. When the tower flange is connected to the external flange, the correct tightening method should be adopted, and no excessive force should be used to avoid cracking the flange. Flange gaskets must not use steel gaskets, and corrosion-resistant and oil-resistant rubber gaskets can be used.
| Copyright © 2015 Hebei Yiyang Antai Environmental Protection Equipment Co., Ltd. - FRP pickling tank | FRP purification tower | FRP desulfurization tower | FRP mixing tank All rights reserved. |
Address: Chengnan Development Zone, Huanghua City, Hebei Province Telephone: 0317-5628177 Mobile: 15233270999
Fax: 0317-5625066 Website: http://cafethera.com Technical Support: Cangzhou Xianyue Network QQ79471598